- BrandТ КОРП ГРУП
- Country of manufactureUkraine
VRU-1 introduction distributing device
Are intended for reception and distribution of the electric power, protection of the equipment against overloads and currents of short circuit in alternating current mains of 380/220 V, with a frequency of 50 and 60 Hz.
- Height above sea level – no more than 2000 m;
- Temperature of air is from +10 With to 350 C;
- Group of service conditions regarding influence of the environment of Sq.m in accordance with GOST 17516.1-90.
Are completed from separate panels according to the questionnaire (in the absence of the questionnaire of the VRU1 panel are delivered with metering devices and devices of protection which parameters correspond to their normal values).
Account devices are installed in the LIE panels. Blocks of automatic and non-automatic control of lighting are used to management of illumination of public networks.
Degree of protection – IRZH – IPOO from a bottom (in accordance with GOST 14254-96).
Climatic modification – UHL, category of placement – GOST 15550-70.
Electric resistance of isolation is not less than 10 megohms.
The busbar of UVR maintains without damages shock current of short circuit not less than 10 kA.
System of tires L1, L2, L3, PEN
Overall dimensions of the panel – 1700kh800kh450mm.
Mass of the VRU1 panel, no more than 155 kg.
Purpose of panels:
introduction ― for the accounting of electric energy;
distributive ― for distribution of electric energy, apply together with introduction;
introduction and distributive ― for distribution and the accounting of electric energy
Structure of a symbol
I LIE - 1
XX ― 2
X ― 3
X ― 4
UHL4 ― 5
1. Introduction distributing device of cupboard execution
2. Classification of panels to destination:
11–18 – introduction;
21–29 – introduction and distributive;
41–50 – distributive
3. Existence of devices on input:
0 – is absent;
1 – the switch on 250A;
2 – the switch on 400A;
5 – the BV block on 250A;
6 – the BPV block on 250A;
7 – the BPV block on 250A and the AVR equipment on 100A;
8 – the BPV block on 250A and the AVR equipment on 250A.
4. Existence of the additional equipment:
0 – is absent;
1 – with groups 30x16A (AE1000) and the equipment of automatic control of lighting;
2 – with groups 30x16A (AE1000) without equipment of automatic control of lighting;
3 – with groups 14x16A (AE1000) and the equipment of automatic control of lighting;
4 – with groups 14x16A (AE1000) without equipment of automatic control of lighting;
5 – with groups 8x16A (E27) and the equipment of automatic control of lighting;
6 – with groups 8x16A (E27) without equipment of automatic control of lighting.
5. A type of climatic modification on GOST15150-69
Standard schemes VRU1.