- Country of manufactureUkraine
Universal podklyucheniy via the smoke channel and an air intake via the airbringing channel outside of the room
The device heating gas household bezdymokhodny - AKGV7.4M, AOGV7.4M, AKGV10M, AOGV10M, AKGV12M, AOGV12M with withdrawal of products of combustion via the smoke channel and an air intake via the airbringing channel outside of the room, is intended for local water heating of inhabited and service premises.
In the devices AKGV10M, AKGV7.4M, AKGV12M in the heat exchanger there is a copper coil for providing with the hot water supply (HWS).
|Device model||The area of the heated room, sq.m||The volume of the heated room, no more, than a m3|
|AKGV7.4M, AOGV7.4M||75||200 … 225|
|AKGV10M, AOGV10M||100||225 … 300|
|AKGV12M, AOGV12M||120||360 … 420|
The device is calculated on application, both in opened, and in closed systems of heating. At installation of the device in the closed system installation on the giving pipeline, to the gate-type gate, the safety valve of nominal pressure of 250 kPa is obligatory.
|Type of gas||natural GOST 5542-87|
|Pressure of gas, Pa (mm w.g.) nominal/minimum/maximum||1274(130)/635 (65)/1764(180)|
|Rated power of kW||7,4±5%||10+5%||12±5%|
|Rated thermal power of an ignition torch, W, no more||250|
|Consumption of gas, m3/h, no more||0,8||1,1||1,34|
|Efficiency in the heating mode, %, not less||85|
|Content of harmful substances in combustion products at the exit in the atmosphere, mg/m3, no more CO NOX||625 240|
|Range of maintenance of temperature of heating of water in the heat exchanger, °C||40... 90|
|Fluctuations of water temperature from set, °C||±5|
|Capacity of the heat exchanger, l||15||18|
|The maximum pressure of water in system of heating, kPa (kgf/cm2), no more||300(3,0)|
|Nominal pressure of water in systems, kPa (kgf/cm2)||200(2,0)|