- Country of manufactureUkraine
Recuperator Reventa RV-3-H
Ventilation unit Reventa RV-3-H was designed specifically for people not wishing to supplement the external facade of the building covers the out of range in the interior. RV-3-H repeats the operation principle model RV-3, but it can be installed without the external cover.
RV-3-H can be installed only in buildings, which will be warmed from the outside. The supply and exhaust air flows are conducted through a duct, the hidden in a heater at least 100 mm thick and is displayed in the window slope, wherein the vent is closed the decorative grille.
Thanks to the RV-3-H, Revent has the ability to offer demanding developers a whole new level of finishing the building facade with no less important for building ventilation without visible outside the covers.
- an inner cover;
- 3D class G3 filter;
- plastic telescopic pipe consisting of stacked rings;
- reversible fan;
- ceramic heat exchanger;
- insulating material;
- a vent;
- ventilation grille.
Recuperator ReVenta RV-3-H - Technical information
|Number of modes||17|
|Number of speeds in reverse||five|
|Noise Level, dB (A)||Rate 1 - 17;
2 Speed - 22;
3 Speed - 33;
4 Speed - 38;
5 Speed - 41
|Displacement ventilation m³ / h||Rate 1 - 19;
2 Speed - 30;
3 Speed - 45;
4 Speed - 55;
5 speed - 63
|Displacement Ventilation Mode "Maximum aeration" m³ / h||100|
|Power consumption at the maximum winding W||4.78|
|type of heat exchanger||high-tech heat accumulator|
|The hole diameter, mm||no less than 235|
|Operating Temperature, ° C||-20 to +50|
|Operating voltage, VDC||7-15|
|dimensions||Composing the minimum tube length - 300 mm.
Diameter - 226 mm.
The inner lid: diameter - 240 mm.
Outer cover: height - 290 mm.
Width - 280 mm.
The outdoor air duct - 500 * 250 * 60.
|method of placement||horizontal arrangement in the outer wall|
|Service||The filter does not require replacement. Cartridge with heat storage and filter should be checked for the need for cleaning every 3 months.|