- Country of manufactureUkraine
- Productivity600 m³/h
Existence: Is available
The BEHTC VUT forced-air and exhaust installation of 600 G with a productivity up to 2200 m3/h in the compact warm and soundproofed case.
The BEHTC VUT forced-air and exhaust installation of 600 G represents completely ready ventilating unit providing a filtration, supply of fresh air to the room and removal polluted, at the same time installation provides transfer of heat of exhaust air to stitched air through a lamellar recuperator. Are intended for connection with round air ducts.
Design of forced-air and exhaust installation: the case is manufactured of the aluminum shape and a sandwich panels with internal warm and sound insulation from mineral wool 20 mm thick.
For a filtration of stitched and exhaust air in installation there are two built-in filters with extent of cleaning of G4 (on an extract) and F7 (on inflow).
BEHTC VUT of 600 G is equipped stitched and exhaust with centrifugal fans of bilateral absorption with the shovels bent forward and the built-in thermostat of protection with automatic restart. Electric motors and driving wheels are dynamically balanced in two planes.
In VUT of 600 G the recuperator of cross current executed from aluminum plates is applied. For operation of installation without recovery the "summer" insert is provided. Under the block of a recuperator the pallet for collecting and removal of condensate is located. Forced-air and exhaust installation is completed with the built-in system of protection of a recuperator against frosting during the cold period of year.
The speed control of rotation of fans is exercised by means of the four-position switch allowing to choose the minimum, average or maximum speed or to switch off installation.
Forced-air and exhaust installation is mounted on a floor, suspended to a ceiling by means of an assembly corner with a vibroinsert or fastens on a wall by means of arms. Installation can be placed both in auxiliary rooms, and basically (behind a false ceiling, in a niche or an open way). It is possible to mount only in such situation to provide collecting and removal of condensate.
Dear clients, pay, please, attention to that fact that electric connection and installation have to be carried out according to the instruction and an electric circuit specified on a terminal box!
|Installation supply voltage, In/50 Hz||1 ~ 230|
|Maximum power of fans, W||2 pieces x 195|
|Current of fans, And||2 pieces x 0,86|
|Total power of installation, W||390|
|Total current of installation, And||1,72|
|Max. consumption of air, m3/h||600|
|Frequency of rotation, min.-1||1350|
|Level of sound pressure on rasst. 3 m, dB(A)||32-48|
|Speed. the moved air, °C||from-25 to +55|
|Isolation||25 mm min. cotton wool|
|Diameter of the connected air duct, mm||200|
|Efficiency of recovery||to 85%|
|Recuperator type||cross current|