- Country of manufactureUkraine
- Productivity400 m³/h
The BEHTC VUT forced-air and exhaust installation of 400 G of the EU represents completely ready ventilating unit providing a filtration, supply of fresh air to the room and removal polluted, at the same time installation provides transfer of heat of exhaust air to stitched air through a lamellar recuperator. Are intended for connection with round air ducts.
Design of the BEHTC VUT forced-air and exhaust installation of 400 G of the EU: The case is manufactured of the aluminum shape and a sandwich panels with internal warm and sound insulation from mineral wool 20 mm thick.
Filter: high extent of purification of stitched and exhaust air is reached at the expense of two built-in filters with extent of cleaning of G4 (on an extract) and F7 (on inflow).
Engine: The highly effective electronic motors switched (EU) with an external rotor are used. Such motors are the most advanced decision in the field of energy saving today. Motors are characterized by the EU
high efficiency and optimum control in all range of speeds of rotation.
In the VUT installation of 400 G Esprimenyaetsya the countercurrent recuperator executed from polystyrene plates. For operation of installation without recovery the "summer" insert is provided. Under the block of a recuperator the pallet is located
for collecting and removal of condensate. Forced-air and exhaust installation is completed with the built-in system of protection of a recuperator against frosting during the cold period of year.
Management: Modification of VUT of of the EU is equipped with the regulator of speed A2 (P-1/010). Control of installation in this case is exercised by means of a signal of 0-10 Century.
Installation: Forced-air and exhaust installation is mounted on a floor, suspended to a ceiling by means of an assembly corner with a vibroinsert or fastens on a wall by means of arms. Installation can be placed both in auxiliary rooms, and basically (behind a false ceiling, in a niche or an open way). It is possible to mount only in such situation to provide collecting and removal of condensate.
Dear clients, pay, please, attention to that fact that electric connection and installation have to be carried out according to the instruction and an electric circuit specified on a terminal box!
|Installation supply voltage, In/50 Hz||1 ~ 230|
|Maximum power of fans, W||2 pieces h175|
|Current of fans, And||2 pieces x 1,3|
|Total power of installation, W||350|
|Total current of installation, And||2,6|
|Max. consumption of air, m3/h||400|
|Frequency of rotation, min.-1||1340|
|Level of sound pressure on rasst. 3 m, dB(A)||28-47|
|Speed. the moved air, °C||from-25 to +60|
|Isolation||25 mm min. cotton wool|
|Diameter of the connected air duct, mm||200|
|Efficiency of recovery||to 95|