- Country of manufactureUkraine
LLC ASR-GROUP offers the BEHTC VUT forced-air and exhaust installation of 200 G on sale pass with a productivity up to 300 m3/h in a compact zvuko-and the heatisolated case with the horizontal direction of branch pipes.
The BEHTC VUT forced-air and exhaust installation of 200 G pass represents completely ready ventilating unit providing a filtration, supply of fresh air to the room and removal polluted, at the same time warmly exhaust air it is transmitted to stitched air through a lamellar recuperator. All models are intended for connection with round air ducts with a nominal diameter of 100 mm, 125 mm.
VUT G pass - models with the horizontal direction of branch pipes, fans with asynchronous motors.
Design of the BEHTC VUT forced-air and exhaust installation of 200 G pass: the case is manufactured of steel with an alyumotsinkovy covering, with internal warm and sound insulation in the form of a layer of mineral wool 20 mm thick.
For a filtration of stitched and exhaust air in installation there are two built-in filters with extent of cleaning of G4. Installation is equipped with the stitched and exhaust centrifugal fan with recurved shovels and the built-in thermostat of protection with automatic restart.
The lamellar recuperator is executed from aluminum plates. For operation of installation without recuperator the "summer" insert is provided. Under the block of a recuperator the pallet for collecting and removal of condensate is located, there is a built-in system of protection of a recuperator against frosting.
Management: inclusion and control of productivity is exercised by means of the thyristor regulator of turns of the engine (PC-1-400) which allows to change smoothly the speed of rotation of the fan in the range of 0-100%.
It is possible to mount forced-air and exhaust installation on a floor, to suspend to a ceiling by means of an assembly corner with a vibroinsert or to fix on a wall by means of arms. Installation can be mounted only in that situation to provide collecting and removal of condensate.
Dear clients, pay, please, attention to that fact that electric connection and installation have to be carried out according to the instruction and an electric circuit specified on a terminal box!
Delivery of the ventilating equipment is carried out to any region of Ukraine. For this purpose you need to choose only the most convenient for you a way of delivery .
On all questions which at you arose concerning acquisition of the BEHTC VUT forced-air and exhaust installation , please, address our specialists in contact phones .
Do the order!Characteristics
|The producer -||VENTS|
|Installation supply voltage, In/50 Hz||1 ~ 230|
|Maximum power of the fan, W||2 pieces h58|
|Fan current, And||2 pieces h0.26|
|Total power of installation, kW||116|
|Total current of installation, And||0.52|
|Maximum consumption of air, m3/h||200|
|Frequency of rotation, min.-1||2500|
|Level of sound pressure on rasst. 3 m, dB(A)||24-45|
|The maximum temperature of the moved air, °C||from-25 to +50|
|Isolation||20 mm, min. cotton wool|
|Filter: extract/inflow||cassette G4|
|Replaceable filter||The Federation Council of VUT pass G4|
|Summer insert||VL VUT pass|
|Diameter of the connected air duct, mm||100|
|Recuperator type||cross current|
|Efficiency of recovery||to 85%|