The system of complex cleaning RFK-1054-CI is counted for small apartments / private houses with small water consumption and constant quantity living 2-3 persons.
This system is intended for removal from water:
- rigidity salts (to 15 mg-ekv/l);
- gland (to 10 mg/l);
- manganese (to 2 mg/l);
- ammonium (to 4 mg/l);
- oxidability (to 10 mgo2/l).
The system represents the filter manufactured of corrosion-resistant high-strength plastic with established on it automatic the managing director of the valve of the peninsula of ClackCorp. (USA). Also salt tank is included in the package of delivery.
The automatic operating valve often still is called "brains" of system. He is responsible for all processes of water purification, restoration of properties of the filtering loading and thanks to it the system works completely independently, excepting influence of "a human factor".
The operating valve is completed with the built-in counter of water and provides automatic regeneration (washing) of system according to the set cyclogram.
Regeneration — restoration of working properties of the filtering material, is carried out in the automatic mode with use (tableted) salt pressed in tablets and waters. Solution of salt is passed through the filtering material, and remote pollution are washed away in the sewerage.
Frequency of regeneration is defined by a filter run (volume of the purified water) which pays off the program of the controller proceeding from chemical and physical indicators of water at adjustment of system.
As the filtering loading specially developed filtering loading of ECOMIX differing in universality and reliability in operation is used. In process of accumulation in a layer of loading of salts of rigidity, iron and manganese regeneration (washing) of loading is carried out. Regeneration of loading of ECOMIX is carried out with use of the tableted salt.
Service of system consists in periodic replenishment of the tableted salt in a tank to a solerastvoritela, and also check and correction of installations of the current time at long interruptions of power supply.
Technical characteristics of system of complex water purification of RFK-1054-CI:
|Overall dimensions (assembly zone), V x Sh x, cm||165 x 100 x 60|
|Height of connections, cm||143|
|Case of a cylinder, V x D, cm||
139 x 26
|The cylinder case with the valve of management, V x D, cm||157 x 26|
|Productivity is working/maximum, m3/hour||1,3 - 1,8|
|The volume of the filtering material, l||37,0|
|Resource of system before the following regeneration (washing), m3 (at rigidity 5 mg-ekv/l)||5,2 *|
|Salt consumption on regeneration, kg||3,7 - 5,6 *|
|Water consumption on regeneration (volume of drains), m3||0,3 - 0,5 *|
|Duration of regeneration, min.||80 - 110 *|
|The term of work of the filtering material, year||to 10|
|Pressure difference in an operating mode, bar||0,28|
|Working pressure, atm||
|Temperature of initial water, 0C||4 - 30|
|The required level of cleaning of mechanical impurity, micron||min. 100|
|Power consumption||220 V / 50 Hz|
|Power consumption, W||30|
|Diameter of connection of pipelines, inch||1"|
|Diameter of connection of the sewerage, inch||3/4"|