- Country of manufactureCzech Republic
- Designation of boilerTwo-circuit (heating+dhw)
- Installation methodWall mounted
Tiger - a series of wall double-circuit gas coppers PROTHERM with a power of 12 and 24 kW for heating and preparation of hot water in the built-in 45 liter accumulative boiler. Are intended for installation in apartments, houses and country houses.
By means of the liquid crystal display it is possible to obtain continuously information at any moment of work of a copper. The display allows to control all process of work constantly. The Tiger model 24 KTZ is equipped with coaxial system of flue gases and does not demand connection to a flue that allows to establish it in rooms where there is no stationary flue or its installation is strongly complicated or impossible due to various reasons.
|Parameters||24 KTZ||24 KOZ||12 KTZ||12 KOZ|
|Fuel||natural gas / propane||natural gas / propane||natural gas / propane||natural gas / propane|
|Al. tension/frequency, In/Hz||230/50||230/50||230/50||230/50|
|Al. power consumption, W||145||105||145||105|
|Degree of protection, IP||44||44||44||44|
|min/move pressure of OV, kPa||100/300||100/300||100/300||100/300|
|Working temperature of OV, °C||45-85||45-85||45-85||45-85|
|Volume of a broad tank of OV, l||6||6||6||6|
|min/move pressure of GVS, kPa||100/600||100/600||100/600||100/600|
|Range of temperatures, °C||40-60||40-60||40-60||40-60|
|Volume of a broad tank of GVS, l||2||2||2||2|
|Expense of the consumed GVS, l/min.||13,6||13,6||10,8||10,8|
|Time of the first heating of an accumulative tank (from 15 °C to 60 °C), mines||10||10||18||18|
|Time of additional heating of an accumulative tank (from 30 °C to 60 °C), mines||7||7||12||12|
|Nominal volume of an accumulative tank, l||45||45||45||45|
|Withdrawal of products of combustion, way||turbo||in a flue||turbo||in a flue|
|Diameter of a flue, mm||60/100||60/100||60/100||60/100|
|Weight without water, kg||70||70||65||65|
OV - heating water, GVS - hot water.