- Country of manufactureCzech Republic
- Designation of boilerTwo-circuit (heating+dhw)
- Installation methodWall mounted
Wall gas coppers of Protherm "Tiger" represent the heating equipment of the increased comfort, and are intended for heating, and also for preparation of hot water in the built-in boiler of 45 liters.
The model range is made by the 12 kW coppers (12 KOZ, 12 KTZ) and 24 kW (24 KOZ, 24 KTZ).
|Parameters||24 KTZ||24 KOZ||12 KTZ||12 KOZ|
|Fuel||natural gas / propane||natural gas / propane||natural gas / propane||natural gas / propane|
|Al. tension/frequency, In/Hz||230/50||230/50||230/50||230/50|
|Al. power consumption, W||145||105||145||105|
|Degree of protection, IP||44||44||44||44|
|min/move pressure of OV, kPa||100/300||100/300||100/300||100/300|
|Working temperature of OV, °C||45-85||45-85||45-85||45-85|
|Volume of a broad tank of OV, l||6||6||6||6|
|min/move pressure of GVS, kPa||100/600||100/600||100/600||100/600|
|Range of temperatures, °C||40-60||40-60||40-60||40-60|
|Volume of a broad tank of GVS, l||2||2||2||2|
|Expense of the consumed GVS, l/min.||13,6||13,6||10,8||10,8|
|Time of the first heating of an accumulative tank (from 15 °C to 60 °C), mines||10||10||18||18|
|Time of additional heating of an accumulative tank (from 30 °C to 60 °C), mines||7||7||12||12|
|Nominal volume of an accumulative tank, l||45||45||45||45|
|Withdrawal of products of combustion, way||turbo||in a flue||turbo||in a flue|
|Diameter of a flue, mm||60/100||60/100||60/100||60/100|
|Weight without water, kg||70||70||65||65|
OV - heating water, GVS - hot water.