- Country of manufactureUkraine
- Principle of air supplyVentilator
COOLERS 2BVG-36 "VIRTUOSO"
The block ventilatory coolers 2BVG-36 "VIRTUOSO" are protected by the patent, the trademark.
Thermal calculation of the cooler, structural design, the choice of materials and components are executed according to technical requirements. In a design of the cooler only materials of the highest class and the mechanical equipment, reliability robots of which are used it was checked by time. Final optimal design decisions represent themselves a combination of modern methods of offered based on computer technologies with long-term operational practice
|Name of parameter||Measurement unit.||Value|
|Productivity on water||m3/hour||130-400|
(Film + mesh layer)
|Temperature of the entering water||°C||No more than 65|
|Temperature of chilled water||°C||t * + (4÷6)|
|Temperature difference, Δt||°C||5÷20|
|Thermal loading at Δt=10 °C||kW||1520 ÷ 4660|
|Drop carrying out||%||≤0,01|
|Pressure in system of water distribution||m.vod.st||3-5|
|Standard of thermal calculation||CTI ATC 105|
|Type of the cooler||Counterflow exhaust|
|Quantity of sections||piece.||1|
|Arrangement of sections||Linear|
|Overall dimensions of the cooler (shir. dl.)||m||3,6х7,2|
|General height of the cooler||m||5,10|
|Height of water distribution system||m||2,80|
|Height of airentrance windows||m||0,97|
|Quantity of flanges of input of water, Du||mm||4x150|
|Area of irrigation||sq.m||25,92|
|Number of fans||piece.||1|
|Brand of the electric motor||ACBO5K|
|Type of connection of the motor and fan||Direct drive|
|Diameter of the fan||mm||2400|
|Material of blades||Fibreglass|
|Noise level (10 meters from the cooler)||dB||65|
|Electric motor parameters||In/Hz / F||380/50/3|
|Rated power of the electric motor||kW||2kh (9-13)|
|Protection of the electric motor||IP54|
t * - air temperature on the "wet" thermometer
The framework of the cooler consists of the metalwork mounted on an installation site. All internal and external metalwork of the cooler is processed by a special highly effective anticorrosive covering. The covering of the cooler consists of profile sheets PASSES. The roof of this cooler consists of four segments made of the polyester reinforced by fiber glass and are established at an angle, forming, thus, a confusor.
The polymeric sprinkler provides high effect of cooling of water at low aerodynamic resistance, we do not litter, is steady against low air temperatures.
In the top part of the cooler the ventilatory installation providing air supply is located. The driving wheel with plastic blades, the diffuser and 9 or 13 kW-ny (depending on the required cooling ability) the electric motor is a part of ventilatory installation.
For providing an optimum operating mode of the electric motor and the most ventilatory installation depending on atmospheric parameters and temperature of chilled water the cooler is completed with a control system and control with is frequency the adjustable electric drive that considerably reduces a power consumption. Vodorasprndelitelny to system of this cooler in plastic execution
The cooler is delivered to full factory readiness in unassembled form (separate assembly units) by the motor transport. Is established on previously prepared pool or becomes attached to already existing. Time of installation of the cooler on the prepared pool 4÷7 days.