- Country of manufactureItaly
- Voltage220~240 В V
The mechanical room Cewal RQ thermostat in the square case intended for installation indoors on a wall also operates heating of the room or cooling for achievement of the most comfortable temperature.
Thermostats of the RQ series can work with any sources of heat using gas as fuel, fuel oil or the electric power are infrared heaters, convectors, electric radiators and other. The room RQ thermostat allows to establish temperature in the range from +5 to +30 °C with sensitivity of 1 °C.
As the thermostat provides economy on heating or cooling:
- The system of heating or cooling is connected to the thermostat in a rupture of connection.
- The thermostat is installed indoors on a wall according to requirements.
- On the thermostat you expose the necessary temperatrura of air in the room (it will measure it in that place where the thermostat is installed).
- At achievement of the air temperature exposed by you the thermostat automatically disconnects system of heating or cooling.
- At decrease in a temperartura of air is lower you established on 1C the thermostat automatically includes system.
- For additional economy we advise not to forget to regulate temperature on the thermostat depending on weather conditions behind a window, and also in the absence to reduce temperature indoors.
Thus the thermostat will be able to save in addition up to 30-40%, and even it is more than funds for heating or cooling of rooms.
SPECIFICATIONS of the RQ series
The thermostat unipolar with independent electric installation
Area of regulation: +5 - + 30 °C
16 (2,5) A 250B for the RQ01-RQ10 models (*)
10 (1,5) A 250B for the RQ05-RQ20-RQ30-RQ35 models
Temperature error: t ≤ 1K
Temperature coefficient: 1K/15 min.
Sensitive element: a chamber for steam expansion
Class I device
Degree of protection: IP 20
Contacts silver 1000/1000
Action of type 1B
The closing and switching contacts
Country of origin: Italy.
(*) Loading 16 (2,5) A 250B it is caused by application for from association of flexible conductors. In case of application
the niya of unbending conductors loading has to be lowered to 10 (1,5) A 250B.
PLACEMENT OF CEWAL RQ01
It is recommended to choose for placement of the thermostat of a zone which in the best way reflect conditions of average temperature of all room. It is necessary to avoid its placement of doors, windows, sources of heat, places with superfluous or lack of ventilation in close proximity
Besides, it is recommended to mount the thermostat at distance about 1,5 m from a floor.
INSTALLATION of the CEWAL RQ01 thermostat (see an intsruktion)
1. To use for fastening a box of the electrical unit with interaxal distances between openings 60 mm as alternative, the thermostat can be attached to a wall (always with interaxal distances between openings of 60 mm);
2. To remove the handle and screws the maintenance of a cover as it is specified on the drawing below;
3. a) to attach a socle to a wall
b) to connect grounding of the device with the help to a clip designated by the corresponding symbol
c) according to the electric circuit given on a cover to attach flexible integral cables in corresponding clips screws
e) to return into place screws, a cover and the handle.
Photo - an intsruktion of connection of the CEWAL RQ01 thermostat
It is possible to buy the CEWAL RQ01 thermostat in Ukraine here, having put goods in a basket, further our manager will contact you for further specification of details of the order.
Delivery is carried out across all Ukraine by popular delivery services in coordination.
Payment is possible as with an advance payment cash or non-cash payment, and upon delivery when receiving by cash on delivery.